[20100324 23:13] We are currently experiencing a utility power failure (due to high winds) and are running on generator power.
[20100325 00:36] Utility power has been restored. We will automatically switch back after it’s stable for 15 minutes.
[20100325 00:50] Everything is back to normal.
The cause was part of a tree breaking off from the high winds and falling into the power lines at the corner of Delucchi and S. Virginia:
View Power outage Mar. 24 in a larger map
We are now taking orders for dedicated servers! Please see http://rollernet.us/services/servers.php for pricing details. To order a dedicated server please contact us by email at email@example.com or by phone at +1.775.284.0383.
A factory technician from Eaton Powerware will be on site Friday, March 12 in an attempt to track down a harmonic distortion issue that is conflicting with the voltage regulator in our generator. Because of the nature of any major UPS maintenance, there is an inherent risk that the critical load may be dropped during transfers to and from maintenance bypass. We will closely monitor our facility during this time.
[20100312 11:37] We have switched to maintenance bypass.
[20100312 15:03] Maintenance bypass has been switched off, however we will be switching to generator for testing.
[20100312 17:05] Back on normal. We will be performing a one-hour “lights out” test later tonight to simulate a utility failure and allow the system to perform automatically.
[20100317 18:00] All tests were successful.
We are scheduled to have our supplemental Sprint DS3 start passing traffic on Thursday, March 11 after 13:00 UTC-8. The circuit is currently up, however its BGP neighbor is not active. We do not anticipate any negative impact from this event.
[Mar. 11, 13:10] Turn up was successful and the DS3 is now passing traffic. Time to completion was approximately 8 minutes.